Concrete pad over tanks.
Bent cleanout cap.
Fallen tree next to cleanout pipe.
Broken cleanout cap at grease trap.
Wiring conduit broken at building. Not sure if the is for the pump station or not.
This conduit may be the pump station wiring.
Deteriorated concrete around pipe leaving pump station.
Broken, corroded wire connectors in pump station.
Broken cap on pipe at pump station.
Deteriorated concrete in pump station with rebar showing through.
Deteriorated concrete, broken pipe. baffle in poor condition and low water level in last septic tank.
Taped wire connections in pump station.
Wiring unsupported in pump station.
Grease trap piping needs cleaning.
Grease trap water level is low.
Trees and vines around piping system in absorption area.
Overgrown absorption area.
Absorption area overgrown with vines and trees.
Depression in absorption area.
Cleanout on the pressurized absorption area not capped.
Fallen trees around pipe in absorption area.